STRUCTURED WIRING FOR VOICE / DATA SYSTEM
The Contractor shall engage a specialist system integrator to carry out the structured wiring for voice / data system. Wiring to individual points shall be 4-pairs UTP Category 6. The wiring shall be terminated at the outlet end and at patch panel. The system integrator shall test and demonstrate on site, to the satisfaction of the engineer and the client, that the wiring is in full compliance with the specific requirements of a Category 6 installation. All wiring shall comply with TIA / EIA TSB-36 and TSB40.
DISTRIBUTION OF VOICE / DATA SYSTEM
Distribution shall be through the GI trunking and drop to the outlets through the concealed PVC conduits or purpose-made riser trunking to Dado / Skirting trunking along with appropriate cable basket as shown in the details to the floor boxes. All conductors in each cable should be connected to a single RJ45 socket at the work area outlets and patch panel at the voice / data rack.